Scope of application CLBISO series rotary isolation switch is mainly used for line isolation between photovoltaic components and inverters in photovoltaic power generation systems. The waterproof performance of this product reaches IP66. The inner c
Scope of application
CLBISO series rotary isolation switch is mainly used for line isolation between photovoltaic components and inverters in photovoltaic power generation systems. The waterproof performance of this product reaches IP66. The inner core of the DC disconnect switch can be installed inside the inverter for the control of the incoming line of the inverter.
● The altitude is 2000 meters and below. Above 2000 meters, derating is required. For other special requirements, please contact the manufacturer:
● The ambient air temperature is -25 ℃ to + 40 ℃, and the average temperature within 24 hours does not exceed + 35 ℃;
● When the ambient air temperature is higher than +40 degrees or hell -25 degrees, please contact the manufacturer;
● The inner core of the product is installed in the distribution box, and there should be a place with waterproof measures.
A1l photovoltaic installations must have a DC Switch to disconnect the DC/AC inverter from the photovolaic panels in accordance with IEC 60947-3.
The switch has 4 separate poles.
Links can be used to change the way that the poles are connected. Links can be used to change the way that the poles are connected.
Interconnection of the poles dominates the load that the switch can connect and break.
As the number of poles increases, the total load switching capacity of the device increases.
It is important to ensure that allelectrical connections (including factory connections) are tight enough that all terminal screws are tightened firmly.
It is recommended that for DC, multi-stranded cable, crimp ferules are used to ensure that the wires do not become loose. Loose cables can cause excessive watt loss and generate excessive heat causing serious damage to the switch.
After instaling and wiring the switch, the testing switches, on and off several times, are necessary for users and user must feel and hear the positive snap actions.
If the switch cannot be felt and heard to operate correctly then it is important that the switch i-s cannot be instaled.